Pesquisar nas perguntas frequentes (FAQ)
NetBotz leak event takes a long time to clear on leak rope sensor after it appears to have dried.
NetBotz leak event takes a long time to clear after leak rope sensor appears to have dried.
NetBotz Rack Monitors w/ Leak Rope Port
NetBotz 4xx and 5xx appliances
NetBotz Leak Rope sensor NBES0308 / NBES0309
After an alert has been triggered on a leak rope sensor, the triggering event must first be resolved before it clears. If the sensor has actually detected water, it will need to dry out completely. If the sensor has been “shorted” to test the event, it will need to be returned to the default state. Once the triggering event is cleared, there is a 30 minute software delay before the alert will clear on the NetBotz unit.
This is being looked into and the event clear time may be addressed in a future firmware revision.
Publicado para:APC Portugal
Isto foi útil?
Precisa de ajuda?
Centro de suporte técnico
Obtenha respostas por si só, experimentando as nossas ferramentas de suporte digital.
Pesquisar nas perguntas mais frequentes (FAQ)
Obtenha as respostas de que necessita explorando as perguntas frequentes (FAQ) relacionadas com tópicos.
Encontre a sua bateria de substituição
Encontre a Bateria de Substituição genuína da APC para a sua UPS.