AP9613 Status LED Behavior Explanation
What does the LED indicator on the AP9613 Dry Contact I/O SmartSlot card indicate?
- UPS Device Management
- AP9613 Dry Contact I/O SmartSlot Card
- v101 firmware
- All serial numbers
The current status LED behavior is for reference and to clarify what is in the user's guide. Refer to the information below.
|AP9613 is booting or starting up||Flashing/Blinking Green|
|UPS Communication Error/Lost Communication with UPS|
|Universal I/O (UIO) error and/or Lost Communication with UIO Accessory|
|AP9613 Hardware Error|
|Configuration Error - Invalid configuration file on the AP9613||Rapid Flashing/Blinking Red|
|UPS "Fault" (as outlined in knowledge base FA171541)||Solid Red|
|Normal Operation||Solid Green|
In order to verify the status of the AP9613 and it's configuration, the Dry Contact I/O SmartSlot Configuration Utility can be accessed via the USB connection as per the instructions in the user's guide.