Why Node-red embedded with Ecostruxure Augmented Operator Advisor stop few second after starting?
After few second, you can see that Node-red stop working
How to diagnostic
When you start AOA, there is one MS-dos windows with a lot of information
In this exemple, you can see that the problem occur after flow starting and after more details about which flow create this error
How to solve the problem
This flow error avoid to start Node-red.
So, we will see how to restart with the previous working flow
Go to …Schneider-electric \ Ecostruxure Augmented Operator Advisor \ Node-red \ node-red home
In this folder you can see the current flow and also the last backup
The propose is to reuse the backup (the last working flow) and delete or rename the current flow (the flow creating node-red crash)
- Change the name or remove the flow named flow_W7FRN05933L.json
- Change the name of the backup .flow_W7FRN05933L.json.backup to flow_W7FRN05933L.json
- Restart node-red
Released for:APC Denmark
Did this answer your question?