Video : How to set the sensitivity in Back-UPS BR1000-IN ?
> Ensure that the Back-UPS is Off but connected to utility power.
> Ensure that the Load's are not connected with the Back-UPS.
Follow the below steps:
Press the front panel push button fully inward for 10 seconds. All indicators on the Back-UPS will flash to acknowledge going into Programming Mode ,The Back-UPS will then indicate its current Sensitivity Setting
To select the Low Sensitivity setting, press the push button until the yellow,indicator is flashing.
To select the Medium Sensitivity setting, press the pushbutton until the yellow and red indicators (second and third from the top) are flashing.
To select the High Sensitivity setting, press the pushbutton until yellow and both red indicators (bottom three) are flashing.
To exit without changing the Sensitivity Setting, press the pushbutton until the green indicator is flashing.
Once in Programming Mode, if the pushbutton is not pressed within 5 seconds, the Back-UPS will exit Programming Mode; all indicators will extinguish.
Please find the video below which will help you to understand the steps easily.