NetworkAIR Legacy Dataguard 5 Common Alarm Facts
Airflow, AFX, CCT, TechCool (TC), and Ceiling Mount (CM), Datatech (DT)
Data Center Cooling
The wire connections may vary, so reference the wiring schematic for your specific product [see attachment].
|EEPROM Fail >||OFF||OFF|
|Ret Hi Temp>||ON||OFF|
The first column (before the >) is the event. If that event has an "ON" in the "COM" column, then it will generate a common alarm (Normally Open and Normally Closed will change states) if that event were to happen. If that event has an "OFF" in the "COM" column, then it will not generate a common alarm if that event were to happen.
NOTE: If the power were to go off while the AC is powered on, there will IS NOT A COMMON ALARM GENERATED went the unit comes back on. The unit will go back to same state it was before the power went off and an alarm will appear on the display and red alarm button will be lit.
NOTE:If the AC is powered off after being on from the On-Off button on the display, this will generate a common alarm while it is off if the KEYPAD OFF event is set to "ON" in the "COM" column in the Alarm Menu section.